Smoke visibility and obscuration are critical outputs of a fire simulation. This post reviews how visibility is calculated in FDS, compares the calculation to experimental data, and discusses how smoke is visualized in the new PyroSim Results Viewer and in Smokeview. The comparison of VTT experimental images with predicted smoke visualization using PyroSim/FDS shows remarkably good correlation.
Visibility is the distance that an observer can identify an object relative to the background and obscuration is the amount light intensity is reduced as it passes through smoke. The calculated visibility is often used as an occupant tenability requirement, while obscuration is used to display smoke visually. My goal in this post is to describe and present some background on how visibility and obscuration are calculated in FDS, the core computation engine used in PyroSim. In particular, I wanted to verify that the new PyroSim Results Viewer correctly reads FDS results and displays smoke correctly.
In preparing this post, my primary references for FDS implementation and experimental validation are: the FDS User Guide (McGrattan, et al., 2017), the SMV Verification Guide (Forney, 2017), and the paper Experimental Validation of the FDS Simulations of Smoke and Toxic Gas Concentrations (Rinne, et al., 2007). Background information on measurement of smoke extinction coefficient and visibility is given in the papers: Method for Measuring Smoke from Burning Materials (Gross, et al., 1967), Specific Extinction Coefficient of Flame Generated Smoke (Mulholland and Croarkin, 2000), Evaluation of the Planck mean absorption coefficients for radiation transport through smoke (Widmann, 2003), and Studies on Human Behavior and Tenability in Fire Smoke (Jin, 2007). A general discussion is given by Mulholland (1995) in Smoke Production and Properties.
Smoke Visibility and Obscuration
In a fire calculation using the simple chemistry approach, the smoke is tracked along with all other major products of combustion (Section 17.10.2 of FDS User Guide, McGrattan, et al., 2017). This means that, for every cell in the model, the smoke density is known. The light extinction coefficient, , is the key parameter used to calculate both visibility and light obscuration. The intensity of monochromatic (single wavelength) light passing a distance through smoke is attenuated as follows (equation 1):
where is the incident intensity. The light extinction coefficient can be calculated using the mass specific extinction coefficient and the smoke density (equation 2).
The default FDS value is , with a suggested uncertainty of . This value is recommended for smoke generated by flaming fires by Mulholland and Croarkin (2000), where they summarized the results of seven studies involving 29 fuels. For smoke generated by smouldering (pyrolysis), the value ranges from to , with the smaller value due to the low light absorption of this smoke. All experiments referenced in the Mulholland and Croarkin paper were performed using a wavelength , corresponding to red in the visible spectrum.
Widmann (2003) analyzed data for flaming fires (stoichiometric and overventilated) and found the correlation between wavelength and to be (equation 3):
This is plotted in Figure 1. The visible light spectrum extends from about 400 nm (violet) through 700 nm (red). Evaluating equation 3 at a wavelength of 633 nm (the wavelength used to obtain the default in FDS) gives an extinction coefficient of 7626 m2/kg, which is smaller than the default value used in FDS (8700 m2/kg), but near the recommended lower uncertainty limit.
Once the light extinction coefficient is known, the visibility is calculated using (equation 4):
where Jin (2007) recommends a range for a reflecting sign and for an illuminated sign. The default value used in FDS is . The experiments used to determine these values used signs in a smoke-filled chamber observed from outside through a glass window, so visibility was not affected by smoke irritation. The visibility measurement relied on the test subjects to determine the distance at which the object was no longer visible, not on a measurement of contrast.
We can see that there are several uncertainties in the calculation of obscuration and visibility. There are uncertainties in soot yield, uncertainties in extinction coefficient as a function of soot density, and uncertainties in calculating visibility as a function of extinction coefficient. The default values used in FDS should be considered reasonable for flaming fires and visibility of reflecting signs.
We will now verify the display of smoke in the Results Viewer integrated into PyroSim. The verification problem is based on the smoke_test problem presented in Chapter 3 of the Smokeview Verification Guide (Forney, 2017). Figure 2 shows the model. White obstructions (gray scale 255) are positioned at distances of 0.5, 1.0, 2.0, 3.0, 4.0 and 5.0 m depth. Black patches (gray scale 50) are positioned on the obstructions to evaluate contrast and visibility. The smoke density is uniformly initialized to a value of 7.922E-5 kg/m3. This gives a light extinction coefficient of 0.6889, corresponding to an intensity drop of 0.5 after passing through 1 m of smoke.
The Weber contrast has been discussed by Mulholland (1995) and used experimentally by Cleary (2004). The Weber contrast is calculated by (equation 5):
where is the brightness of the object and is the brightness of the background. Mulholland notes that for a black object viewed against a white background, a value of is often used as the contrast threshold defining visibility.
The expected light intensity of the white obstructions and the black patches are given in Figure 3, including the calculated Weber contrast. In this problem, both the background and the black patch are obscured equally by smoke, so that the intensity of both are reduced identically and the calculated Weber contrast is constant. As will be shown, the visibility is clearly reduced with increased obscuration, so it appears that the Weber contrast is not useful in calculating visibility in such a situation. An additional problem with the Weber contrast is that for a pure black object (gray scale 0), equation 5 will give a constant value of -1.
The FDS and PyroSim Results Viewer of the smoke are shown in Figure 4. The theoretical and displayed values are identical. Based on the extinction coefficient, the visibility is 4.35 m. A careful examination of Figure 4 shows that we can just discern the black patch at a distance of 4.0 m, but cannot identify the patch at 5.0 m, so the visibility calculation matches the display. However, this also demonstrates that the Weber contrast cannot be used to determine visibility in such a case.
It should be noted that in Figure 4, the ambient light was set to zero and camera light was positioned at infinity. Figure 5 shows the results using the default ambient light (0.2) and the default light position at the camera. The ambient light value does not change the intensity of the white obstructions, but the dark gray patches appear somewhat lighter.
VTT Experimental Validation of Visibility
Rinne et al. (2007) at the VTT Research Center of Finland performed a series experiments to validate FDS simulations of smoke and toxic gas concentrations. These calculations were performed using version 4.05 of the Fire Dynamics Simulator (FDS). For this post, we repeated the calculation using FDS version 6.5.3. This model has previously been used in posts discussing fire modeling. In this post, we will focus on the smoke and visibility of the exit signs. Figures 6 and 7 show side and top views of the experiment.
For this study, we simulated the toluene fuel experiment, since that fuel provided experimental data to calculated smoke density. The experimentally measured peak HRR was 145.7 kW, which corresponds to a m. We changed the model to use multiple meshes with a cell size of 5 cm for the fire and opening. This gives a value of approximately 10, which should properly capture entrainment of air in the fire plume. The model is shown in Figure 8. The rgb values of the signs in the model were set to correspond to the rgb values measured from the initial camera image of the experiment.
The original VTT paper gives results for 20 cm and 10 cm meshes. We give two representative graphs that compare results from the original study to the present study. Recall that changes include using FDS version 6.5.3 (version 4.05 in original) and refining the mesh. Figure 9 shows the temperature at a height of 4.5 m. The measure experimental results and the model results are essentially identical for both of the thermocouple trees. Figure 10 compares the CO concentration. Figure 11 compares smoke layer height, which is extracted in FDS using the temperature profile as a function of height. The smoke layer results for the 5 cm case are 10 to 20 cm lower than when measured experimentally.
To compare the visibility and obscuration due to smoke, we can first compare the experimentally measured soot density to the FDS results, Figure 12. The reader is referred to the VTT paper for a full description of the density measurement, but the procedure used equations 1, 2, and 3 to convert light transmission measurements made with a MIREX device to density by calculating the mass specific extinction coefficient as a function of wavelength. As can be seen, the 5 cm results fall within the experimental data range.
We can also make a direct comparison with an image taken by a camera located just outside the vent opening. Figure 13 shows the picture at 6 minutes. This can be compared to the PyroSim image in Figure 14, which displays a slightly lower layer of smoke. We can also see that interior lighting was included in the experiment that helped illuminate the exit sign. As shown by the red hue on the bottom of the smoke layer, the fire also contributed to lighting.
In this post we have accomplished three things:
- We reviewed the procedure used to calculate visibility and obscuration in FDS. Soot density is calculated based on the soot yield defined in the combustion reaction. Soot is then carried through the model, and the density is available at each cell. The light extinction coefficient is calculated using the mass specific extinction coefficient (measured experimentally) and the local soot density. Finally, the visibility is calculated using the Jin correlation with light extinction coefficient.
- We verified obscuration with a problem that used constant soot density and white obstructions located at increasing distance from the viewer. The intensity of the obstructions decreased correctly with the distance that light traveled through the smoke. We also verified the calculated visibility using an image that showed black patches on the white obstructions. For this case, both the black patch and the white background are obscured equally by the smoke, so the Weber contrast is constant and does not seem to be valid for this situation.
- Finally we repeated a simulation of the VTT experiments that measured smoke and toxic gas concentrations. We did this calculation using the current release of FDS and a refined mesh.
Although there are several uncertainties in the calculation of soot density and the conversion of the density to visibility and obscuration, the comparison of VTT experimental images with predicted smoke visualization for the toluene fuel shows remarkably good correlation (Figures 13 and 14). It should be noted that the VTT paper indicates that the predicted obscuration was greater than observed for wood and PMMA fires.
We expect that future development of the results visualization in PyroSim will include options to incorporate interior lights and fire illumination.
Cleary, T. G. (2004). Video Detection and Monitoring of Smoke Conditions, International Conference on Automatic Fire Detection AUBE ’04”, 13th Proceedings. University of Duisburg. [Internationale Konferenz uber Automatischen Brandentdeckung.] (http://ws680.nist.gov/publication/get_pdf.cfm?pub_id=101189).
Forney, G. P. (2017) Smokeview, A Tool for Visualizing Fire Dynamics Simulation Data, Volume III: Verification Guide, NIST Special Publication 1017-3, Sixth Edition, Smokeview Version 6.4.4 (https://pages.nist.gov/fds-smv/manuals.html).
Gross, D., Loftus, J. J., and Robertson, A. F. (1967). Method for Measuring Smoke from Burning Materials, Symposium on Fire Test Methods – Restraint & Smoke 1966, ASTM STP 422, Am. Soc. Testing Mats., 1967, p. 166 (http://fire.nist.gov/bfrlpubs/fire60/PDF/f60002.pdf).
Jin, T. (2007). Studies on Human Behavior and Tenability in Fire Smoke, Fire Safety Science, Proceedings of the Fifth International Symposium, pp 3-21 (http://www.iafss.org/publications/fss/5/3/view/fss_5-3.pdf).
McGrattan, K., et al. (2017). Fire Dynamics Simulator User’s Guide, NIST Special Publication 1019, Sixth Edition, FDS Version 6.5.3 (https://pages.nist.gov/fds-smv/manuals.html).
McGrattan, K., et al. (2017). Fire Dynamics Simulator Technical Reference Guide Volume 1: Mathematical Model , NIST Special Publication 1018-1, Sixth Edition (https://pages.nist.gov/fds-smv/manuals.html).
Mulholland, G. W. (1995) Smoke Production and Properties, in DiNenno, P.J., et al., Editors, SFPE Handbook of Fire Protection Engineering, 2nd Edition, Chapter 15, Section 2, pp. 2/217-2/227, (http://fire.nist.gov/bfrlpubs/fire95/PDF/f95126.pdf).
Mulholland, G. W. and Croarkin, C. (2000) Specific Extinction Coefficient of Flame Generated Smoke, Fire and Materials, Vol. 24, No. 5, 227-230, September/October 2000.
Rinne, T., Hietaniemi, J. and Hostikka, S. (2007) Experimental Validation of the FDS Simulations of Smoke and Toxic Gas Concentrations, VTT WORKING PAPERS 66, ESPOO 2007, ISBN 978-951-38-6617-4 (go to http://www.vtt.fi/publications/index.jsp and search for the title).
Widmann, J. F. (2003). Evaluation of the Planck mean absorption coefficients for radiation transport through smoke, Combustion Science and Technology, 175:12, 2299-2308, DOI: 10.1080/714923279
One initial source of confusion for me was the difference between the thermal radiation calculation and the visibility/obscuration calculation. The calculation of thermal radiation in the energy equation is completely independent of the visibility and obscuration calculation, Section 2.6.2 of FDS Technical Reference Guide (McGrattan, et al., 2017). The default thermal radiation calculation assumes a gray gas model where the radiation absorption coefficient is calculated using the RadCal program. This is similar to the Planck mean absorption coefficient calculated by Widmann (2003) by integrating over all wavelengths.
Download PyroSim Input Files
Here is a zip file of the PyroSim input files.
Comments or Questions
This post was written by Daniel Swenson. For comments or questions, send email to email@example.com.
- Original post, 2017-06-19.